How do I program for a 2-wire smoke detector on a DSC 1616, 1832, or 1864 system?
Since 2 wire smoke detectors are only connected to PGM 2, the programming for them is very straightforward.
- Enter programming with *8 followed by the installer code.
- Enter section 009.
- The first 2 numbers that appear here are for PGM 1. We don’t need to change these so you can push the right arrow key twice to scroll to PGM 2.
- Here we’ll enter 04 for the 2 wire smoke PGM definition.
- Press # to exit out of programming.
Keep in mind that all 2 wire smoke detectors must be wired in parallel to PGM 2 and Aux +.